Delphys XL is a highly compact UPS with best in class efficiency offering inherent redundancy and allowing by design, fast & safe maintenance operation. A fully resilient UPS architecture eliminating traditional single points of failure.
The solution for
? Data centres
? Industrial processes
Flexible integration with an optimised footprint
? 1200 kVA/kW packed into a compact and optimised design.
? Highly flexible connection to your electrical environment.
? Easy and fast deployment of the entire UPS system.
? Up to 70% space saving when combined with lithium-ion batteries.
? Advanced on-site testing features to certify commissioning.
Best in class energy management & savings
? 99% efficiency with our Smart Conversion Mode.
? 97% VFI mode as standard.
? ?Hot stand-by? for higher system efficiency under low load conditions.
? Multiple advanced operating and testing mode to minimise TCO.
? Ready for grid support functionalities.
Critical chain interoperability
? Designed to fit any data centre power distribution architecture.
? Advanced functionalities to ensure Genset stability upon restart or significant variation in loads.
? Designed to coordinate perfectly with our downstream connected STS.
? Supports even the most challenging load.
Unmatched resiliency to maximise availability
? UPS architecture eliminates single point of failure related to traditional monolithic UPS.
? Fault tolerant concept provides double conversion mode redundancy up to 80% of the rated power.
? Self-sufficient power bricks with advanced selective disconnection.
? Based on our field proven high power XL platform.
? Limited number of power converters – each designed to eliminate potential fault propagation for best MTBF.
? Powerful and robust static bypass.
Easy and safe maintenance supporting low MTTR
? Reduced MTTR supported by coldextractible power bricks.
? No cabling operation required to slide-out a power brick.
? Front access to all components.
? Safe servicing thanks to ?hands outside? maintenance.
? Maintenance station with embedded operating power brick as a spare.
? Option to test the UPS and batteries without load when carrying out maintenance activities.